Electrical engineering root cause analysis (RCA) related to considered not possible HT motors’ Direction of Rotation (DOR) changed.
|Article Type:||Root Cause Analysis (RCA)|
|Author:||S. Raghava Chari|
Note: This root cause analysis (RCA) is from real-time scenarios that happened in industries during the tenure of two or three decades ago. These articles will help you to improve your troubleshooting skills and knowledge.
HT Motor Direction of Rotation (DOR)
Why Direction of Rotation (DOR) arrows?
Large motors’ come with backward-curved fans (below figure). They deliver max air-flows at marked Direction of Rotation (DOR) and very little in the opposite DOR.
Consequently, the winding temperature could go a lot higher than permitted. It could shorten winding lives even lead to burnouts. This is especially serious, as most motors have no winding temperature indicators (at that time). Hence, DOR marks.
However, one can change DOR to suit the driven machine thus:
- swap the left and right internal axial fans (IAF above-figure)
- Substitute the existing External Radial Fan (ERF) with a purchased or homemade opposite curved vanes fan
- Fix a new DOR indicating arrow
- Interchange the two electrical leads as usual
Benefits of the RCA learned know-how
The plant used surplus motors gainfully and saved purchase costs for new applications.
Author: S. Raghava Chari
Do you face any similar issues? Share with us through the below comments section.
If you liked this article, then please subscribe to our YouTube Channel for Instrumentation, Electrical, PLC, and SCADA video tutorials.
- Problems with Switchgears
- Transformer Problem Solved
- Aluminum Cable Terminations
- Arc Fault Breaker Problem Solved
- Hardware Troubleshooting for PLC