When a voltage is applied to the coil, a current passes through it and this creates a magnetic circuit which includes the core, armature and the yoke. The core attracts the armature, which pivots and presses the push rod against the common contact, breaking the electrical connection with one contact and making the electrical connection with the other contact. When the voltage is removed from the coil the magnetic attraction of the armature to the core ceases. A spring then returns the contacts, pushrod and armature to the initial position. In this example, the common contact also acts as the spring, but in other relays, a separate spring is employed.
The above animation shows that when we apply a voltage to the relay coil, the Relay contacts will change. For example the Normally Open (NO) becomes Normally Closed (NC) and similarly the Normally Closed (NC ) becomes Normally Open (NO). When we remove the applied voltage to the relay coil then the relay contacts again comes into default state.
Simple Relay Schematic :
Design a relay (CR1) circuit which controls two lamps, one is Red lamp (R) and another is Green Lamp (G). These lamps will be controlled by using a single switch (S). When switch is pressed then Red lamp will be ON and Green lamp will be ON during switch de-energised state.
Relay Schematic : When Switch Not Pressed
Circuit Operation :
- When Switch S in Open state
- Relay Coil CR1 will be De-energized
- Relay Contact CR1-1 will be Open (Here Relay NO contact is using in the circuit.)
- Red Lamp will be OFF as relay contact CR1-1 is Normally Open (NO). so circuit open and no current flow.
- Relay Contact CR1-2 will be Closed (Here Relay NC contact is using in the circuit.)
- Green Lamp will be ON as relay contact CR1-2 is Normally Closed (NC). so circuit closes and there is a current flow.
Relay Schematic : When Switch Pressed
Circuit Operation :
- When Switch S in Closed state
- Relay Coil CR1 will be Energized
- Relay Contact CR1-1 will be Closed (Here Relay NO contact is using in the circuit.)
- Red Lamp will be ON as relay contact CR1-1 Normally Open (NO) contact becomes Normally closed as Relay is energized.
- Relay Contact CR1-2 will be Open (Here Relay NC contact is using in the circuit.)
- Green Lamp will be OFF as relay contact CR1-2 Normally Close (NC) contact becomes Normally Open as Relay is energized.
- Analyze the Relay Circuit and Find the Status ?
- Explain Operation of the Lamp Circuit ?
- As per Process Conditions, Find out the Circuit Components Status ?
- Determine the Status of Lamps and Relays in the Circuit ?
- Relay Loop Back Circuit
- PLC Program for Mixing Tank
- Relays in Ladder Logic Tutorials
- Relay circuits
- PLC Program for Conveyor Motor
- PLC Ladder Logic Example