Instrumentation engineering root cause analysis (RCA) of under and over-capacity control valves pose poor controllability.
|Article Type:||Root Cause Analysis (RCA)|
|Equipment Type:||Control Valves|
|Author:||S. Raghava Chari|
Note: This root cause analysis (RCA) is from real-time scenarios that happened in industries during the tenure of two or three decades ago. These articles will help you to improve your troubleshooting skills and knowledge.
Under and Over Capacity Control Valve
Two control valves posed problems (P) and the Author RCA solutions (S) are as under:
Poor boiler drum level control because of just 15% open LCV 301
Obviously poor controllability oversized control valve (CV).
Re-calibrate the 30-mm valve travel VP (valve positioner) for 20 mm travel and fix a new 20 mm marks scale.
Even with exit PCV 213 full open, First Flash Separator pressure was > SP
Obviously, control valve (CV) opening is insufficient;
Re-calibrate the valve positioner (VP) from 35 mm to 55 mm and fit a 55 mm marking scale
Benefits of the Solution
Excellent control, saved new valves purchase costs, and commissioning proceeding on schedule.
Author: S. Raghava Chari
Do you face any similar issues? Share with us through the below comments section.
If you liked this article, then please subscribe to our YouTube Channel for Instrumentation, Electrical, PLC, and SCADA video tutorials.
- Valve Positioners Failed
- Errors and Faults in Siemens PLC
- Repeat Failures of Letdown Valves
- Pressure Taps Block Valves Leaks
- Unstable & Drifting Values of Transmitter