This is PLC Program for Alarm indication in process.
In many industries there are lots of machines which are performing many tasks automatically. There are many sensors and components used in system or process. Sometimes operator may not be identify the problems of machine or system by visual observations. And also sometimes there will be a chance that machine stops working due to some problem in it.
We can solve this problem by adding alarms in system or process. Alarms are added to alert operator to monitor that machine/process about to cross its limit values or already crossed the limit. Alarms are indicated to the operator by annunciator or horns, and lights of different colours on the panel. (For example, green lights meant OK, Yellow meant not OK, and Red meant BAD.)
The purpose of alarms is to use automation to help human operators as they monitor and control processes, and alert them regarding abnormal situations of the plant. Incoming process signals are continuously monitored, and if the value of a given signal moves into an abnormal condition, a visual and/or audio alarm informs the operator regarding the situation.
For our problem discussions, we considered one simple system and configure alarms for the system. For example consider one filling and discharging process and in this system we want to consider some alarms, we will show alarm by using lamps on panel board.
For example, consider following alarms for our system,
- Emergency stop pressed
- Feed valve open error
- Feed valve close error
- Discharge valve open error
- Discharge valve close error
Here all are errors so we take all red color indication as shown in above figure.
Here is PLC program for Alarm indication in process.
List of Inputs/Outputs
- Cycle START=I0.0
- Cycle STOP= I0.1
- Low Level Switch, LL=I0.2
- High Level Switch, LH=I0.3
- Feed VLV open LS=I0.4
- Feed VLV close LS=I0.5
- Disc. VLV open LS=I0.6
- Disc. VLV close LS=I0.7
- Emergency STOP=I1.0
- Cycle ON=Q0.0
- Feed valve=Q0.1
- Disc valve=Q0.2
- Emergency STOP pressed= Q0.4 (Indication lamp)
- Feed VLV open error= Q0.5 (Indication lamp)
- Feed VLV close error=Q0.6 (Indication lamp)
- Disc VLV open error=Q0.7 (Indication lamp)
- Disc VLV close error=Q1.0 (Indication lamp)
Ladder diagram for Alarm indication in process.
In this application, we have used Siemens S7-300 PLC and TIA Portal Software for programming.
Network 1: In network 1, we used latching circuit for cycle ON (Q0.0) output. It can be started by pressing cycle START PB (I0.0) and STOP by pressing STOP PB (I0.1).
When cycle will be START then system checks level of the tank. If tank level is low then the feeding process will start and if tank level reaches high then Discharge cycle will START.
Network2: When tank reaches low level then LL (I0.2) will be activated and feeding cycle will be ON. Here we have taken NC contact of LH (I0.3) so when PLC will detect high level then it will STOP feeding cycle.
Network 3: When tank reaches high level then LH (I0.3) will be activated and discharging cycle will be ON. Here we have taken NC contact of LL (I0.2) so when PLC will detect low level then it will STOP discharge cycle.
Network 4: When system receivies Emergency STOP (I1.0) input then it will activate the Emergency STOP pressed output (Q0.4) and alarm indication will be provded to the operator.
Network 5: In this network we have configured feed VLV open error alarm (Q0.5), when feed valve is ON and Feed VLV open LS (I0.4) is not detected then timer will START and after 5s Feed VLV open error alarm is ON (Q0.5).
Network 6: In this network we have configured feed VLV CLOSE error alarm (Q0.6), when feed valve is CLOSE and Feed VLV CLOSE LS (I0.5) is not detected then timer will START and after 5s Feed VLV CLOSE error alarm is ON (Q0.6).
Network 7: In this network we have configured Disc VLV OPEN error alarm (Q0.7), when disc valve is ON and disc VLV OPEN LS (I0.6) is not detected then timer will START and after 5s disc VLV OPEN error alarm is ON (Q0.7).
Network 8: In this network we have configured Disc VLV CLOSE error alarm (Q1.0), when disc valve is CLOSE and disc VLV CLOSE LS (I0.7) is not detected then timer will start and after 5s disc VLV close error alarm is ON (Q1.0).
Network 9: In this network we have configured BUZZER for all alarms, when alarm detected then BUZZER (Q0.3) will be activated and it can be RESET by pressing RESET (I1.1).
Network 10: Operator can reset the BUZZER by pressing RESET (I1.0)
Note : The above PLC Logic provided for basic idea about application of PLC in Alarm Indication of a Process. The Logic is limited and not complete application.
Author : Bhavesh
- PLC Program for Water filling and Discharging Process
- PLC Program to Control Level of Two Tanks
- PLC Program for Automatic Heating and Mixing of Products
- PLC Program to Control Level of Series Tanks
- PLC Program for Automatic Mixing Controlling in a Tank
- PLC Program for Fan Control Unit System for Industry
- PLC Program for Artificial Fishpond Water Level Monitoring System
- PLC Program to Control Level of Parallel Tanks
- PLC Program for Controlling Conveyors ON Sequence and OFF Sequence
- PLC Program for Burglar Alarm Security System