PLC Latching and unlatching Circuit
This is PLC Program for Latching and unlatched circuit for output.
- In some conveying system operator fills tank manually by operation water pump manually.
- In this situation operator waits when tank is being filled because when tank reaches to high level, water pump should be stopped.
- And also water pump should remain in ON condition until tank reaches the high level.
- For example we consider manual water conveying system in this article.
- In this example we consider one storage tank for water and use one water pump for tank filling.
- We also use one level sensor for high level and control panel for operator.
- Here START PB for enabling the motor so we can feed the water in the tank, for stop motor we use STOP PB.
- Level sensor for detection of High level so when tank becomes full, high level sensor will be activated and stops the water pump.
- For this sequence we will use SET and RESET instruction for latching and unlatching the water pump.
- We can make this circuit by sing relays.
- In application there one manual discharge valve only for discharging the tank manual. We will not consider in or logic.
PLC Inputs List
- START PB : I0.0
- STOP PB : I0.1
- HIGH LEVEL SENSOR : I0.2
- LOW LEVEL SENSOR : I0.3
PLC Outputs List
- WATER PUMP : I0.0
PLC Ladder diagram for Latching and unlatched circuit
- For this application we use S7-1200 PLC and TIA portal software for programming. We can make this circuit or logic with relay also.
- This circuit or logic known as latching and unlatching circuit or logic.
- We will write logic for water pump in Network 1. Here we use NO contact of START PB (I0.0) for enabling the water pump (Q0.0).
- By using SET instruction water pump output coil (Q0.0) will be latched.
- Add NO contact of LEVEL LOW SENSOR (I0.3) in series with the water pump output (Q0.0).
- Water pump should not start if tank is full. so for safety purpose use one NO contact of LOW LEVEL SENSOR (I0.3) in series after START PB (I0.0) in Network 1.
- Now HIGH LEVEL SENSOR (I0.2) will be detected after some time of pump running and in this case water pump (Q0.0) should be stopped automatically. For that purpose we need to unlatch the circuit.
- We will write logic for unlatching circuit in Network 2. In this case, we take No contact of HIGH LEVEL SENSOR (I0.3) for unlatching the circuit by using RESET instruction.
- Add one NO contact of STOP PB (I0.1) in parallel connection, so operator can unlatch the circuit by pressing STOP PB (I0.1).
- Here we latch circuit by SET instruction and unlatch with RESET instruction.
Runtime Test Cases
Note : The above PLC Logic provided for basic idea about application of PLC Program for Latching and unlatching Circuit. The Logic is limited and not complete application.
Author : Bhavesh
Articles You May Like :
- PLC Program for Conditional Control Logic
- PLC Program for Water filling and Discharging Process
- Series Tanks Level Control using PLC Ladder Programming
- 3 Phase Motor Control using PLC Ladder Logic
- PLC Program to Drain Same Products from Two Tanks
- PLC Program for Automatic Mixing Controlling in a Tank
- PLC Permissive for Motor Control
- PLC Level Control of Two Tanks
- PLC Program for Sequential Motor Control
- PLC Program for Water Level Control Logic