Why the Cable Screen shall not be Grounded at instrument field device?
Cable screen protects the signal carried on the conductor from external interference. Cable screen blocks the external interference and noise, then directs it to the ground.
Screen shall only be grounded at one source. The grounding is usually made in equipment panel or cabinet while field device point is left ungrounded and insulated. This is to eliminate the ground-loop current that may arise if screen is grounded at both end. In this case, the ground loop current becomes a noise for the signal conductor itself.
- Where should we Terminate the Cable Shields ?
- Ground Detector Principle
- Single Phase Power Wiring Schemes
- Basics of Ground Loops
- Types of Thermocouple Measuring Junction
- Capacitive Coupling Effects
- How to Avoid Bad Grounds ?
- Floating Vs. Grounded Voltage
- Electrical Wiring Terminology
- 3-Wire, Three-Phase Delta Wiring System