Electric motors permit manual, semi-automatic, and automatic operation of the valve. Motors are used mostly for open-close functions, although they are adaptable to positioning the valve to any point opening as illustrated in Figure 33.
The motor is usually a, reversible, high speed type connected through a gear train to reduce the motor speed and thereby increase the torque at the stem. Direction of motor rotation determines direction of disk motion.
The electrical actuation can be semi-automatic, as when the motor is started by a control system. A handwheel, which can be engaged to the gear train, provides for manual operating of the valve.
Limit switches are normally provided to stop the motor automatically at full open and full closed valve positions. Limit switches are operated either physically by position of the valve or torsionally by torque of the motor.
Figure 33 Electric Motor Actuator
- What is a Electric Motor Actuator ?
- Motor VFD Drive features
- Shunt-Wound Motor Operation
- Manual, Fixed, and Hammer Actuators
- Electrical Actuators
- Self-Actuated Valves, Pneumatic & Hydraulic Actuators
- Starting a Synchronous Motor
- Stepper Motor Working Principle
- Series-Wound Motor
- Difference between Stepper Motor and Servo Motor