Current to Pressure (I/P) Converter Principle :
The I/P Converter works on Flapper/Nozzle principle.
Also Read : What is Flapper/Nozzle System
In the Current to Pressure converter, we usually give input current signal as 4 – 20 mA . We also give a continuous supply of 20 P.S.I to the Flapper Nozzle assembly. As we give input current signal, Electromagnet gets activated. If the current is more, then the power of magnet will get increased. The Flapper of the Flapper-Nozzle instrument is connected to Pivot so that it can move up and down and a magnetic material was attached to other end of flapper and it is kept near the electromagnet.
As the magnet gets activated. the flapper moves towards the electromagnet and the nozzle gets closed to some extent. So the some part of 20 P.S.I supplied will escape through nozzle and remaining pressure will come as output. If the current signal is high, then power of the magnet will increase, then flapper will move closer to the nozzle, so less pressure will escape through nozzle and output pressure increases.
In this way the output pressure will be proportional to the input current.
For the input current of 4 – 20 mA we can get the output pressure of 3 – 15 P.S.I
- Pressure to Current (P/I) Converter Principle
- What is Flapper Nozzle System ?
- Pressure Regulator with Flapper-Nozzle Principle
- Current to Pressure (I/P) Converter Calibration Procedure
- Pneumatic Valve Positioner Working Principle
- Pneumatic Load Cell Principle
- PLC Raw Count Calculation for Pressure Transmitter
- D’Arsonval Meter Movement
- History of 3-15 psi, 10-15 mA, and 4-20 mA signals
- Gage and Absolute Pressure Transmitters Principle